Designed for indoor installation in commercial or industrial applications. Emergency AC power is supplied to lighting fixtures equipped with incandescent, linear fluorescent, compact fluorescent or LED lamps. The lighting load can be installed at a distance of up to 1,000 feet from the LiteGear® central lighting inverter. Observe all required AC conductor sizing requirements. When using LED lamps, consider LED in-rush current in load calculations.
When normal utility supplied power is interrupted, the LiteGear® Series unit will automatically transfer to emergency mode in less than 2-seconds and begin supplying inverted battery-derived AC power to the load for 90 minutes. The unit is capable of operating normally on, normally off or switched loads. A low voltage battery disconnect circuit will prevent “deep discharge” damage to the battery. The charging circuit will bring the batteries to full recharge within UL time standards. A “brownout” circuit will automatically transfer the unit to emergency power if the utility voltage falls to a pre-determined “low line” limit. 125VA/110W and 250VA/220W versions provide pure sine wave output.
The LiteGear® enclosure and cover are constructed of heavy-duty, steel with a white powder-coat paint finish.
UL 924 (Emergency Lighting) UL 2043 (Plenum Air Handling Spaces) for LG125T Life Safety Code (NFPA 101) National Electrical Code (NFPA 70) State and Local Code compliant